DLVP 13: How to configure the Occupancy Sensor Settings
This video will demonstrate how to use the Power Module’s onboard configuration switches to select the desired occupancy sensor operation. For more information visit www.eaton.com/DLVP
Lighting Similar Videos
Eaton's WaveLinx Connected System
Learn how recent updates to the WaveLinx Connected System helps you easily recognize opportunities to decrease building energy usage.
Eaton's LumaWatt Pro Wireless Sensing and Control System
Learn how the LumaWatt Pro solves higher value, complex energy problems by analyzing building utilization.
Shaper 1400 and 1800 architectural LED luminaires
A series of performance pendants that add a flair of interest with a wide selection of color combinations.